Easy assembling excellent structured long lifespan biogas plant filter
Biogas desulfurization equipment is mainly to remove H2S and impurities in biogas. Fill desulfurizer in desulfurization equipment to remove H2S.
Desulfurizer in the desulfurization equipment, the components are mainly Ferric Oxide, and add other efficient purifying material from the processing of additional accelerator. Even in no oxygen and no ammonia environment, it also can remove H2S precisely. It also has effect on removal of thiols organic sulfur and most of the nitrogen oxides.
In purifying performance and operation, the desulfurization equipment is with
1), reasonable structure
2), small bed resistance
3), high sulfur removal
4), easy operation
5), high sulfur capacity penetration
6), strong adaptability of installation site 7), no secondary pollution
8), simple and quick installation etc.
1. Main physical and chemical properties of desulfurizer:
Brown cylindrical bar
Dia5 to 6 Len. 5 to 30mm
Ferric Oxide content
25 to 33 percent
0.85kg per Litre
50 to 60 percent
Not less than 50.0N per cm(Lateral pressure)
2. Main reaction principle of desulfurization
(1) Fe2O3.H2O+3H2S=Fe2S3.H2O+3H2O (2) Fe2O3.H2O+3H2S=2FeS+S+4H2O When desulfurizer is alkaline, reaction is according to formula (1) to right; when desulfurizer is acid, reaction is according to formula (2).
If H2S gas content in the outlet gas of the desulfurization equipment is more than the required value, desulfurizer should be replaced to ensure normal use of desulfurizer and enabling normal operation of the desulfurization equipment.
Desulfurizer usage amount is determined by the following conditions: A, H2S concentration in the feed gas and the gas flow B, Desulfurization tower outlet H2S concentration required value C, Desulfurizer Replacement cycle
Packaging & Shipping
Notice: 1. Do remove the crumb firstly, after pouring out the material of desulphurizer, just remain the granular material. 2. Do not put the material on the plastic or wooden or inflammable products when regenerating. 3. Do not put the crumb material of desulfurizer back to desulphurizer
The following is desulpfurizer’s working principle:
When biogas comes out from plant, there are some steams which can be departed through cooling. The principle of desulfurization: Fe2O3.H2O+3H2S=Fe2S3.H2O+3H2O
after used some times, sufficiency of desulfurization would be decrease. Then we should replace desulfurization or regenerate. The principle of regeneration: 2Fe2S3.H2O+3O2=2Fe2O3.H2O+6S
Shenzhen Puxin Technology Co. Ltd Add: 2nd floor, Bldg 4, 49 Jiaoyu North Rd, Gaoqiao District, Pingdi Street, Longgang, Shenzhen, P. R. China Postal Code: 518117 Tel: +86-755-28938251 86-755-28938252 Fax: +86-755-89323983 Web: http://www.puxintech.com/